Chemolli Fire Systems door, X313 family, with two wooden leaves with wooden frame classified EI1 60 for fire resistant according to EN 13501-2:2007 + A1:2009 with resistance to hot smokes according to UNI EN 13501-2:2016.
Chemolli Fire Systems door, X313 family, with two wooden leaves with wooden frame classified EI1 60 for fire resistance according to EN 13501-2:2007 + A1:2009.
The family of doors, in the various versions, has passed the test according to the following reports:
Test report (Fire) 2016CS01330 released on 15/07/2016 From Rina Services lab.
Classification report (Smokes) N.007-2020-CLF released on 17/04/2020 from Z Lab.
80 mm thick hinged door, honeycomb core with internal insulation, structure and rebates in solid wood, covered in MDF. Finished with melamine edge. Solid wood frame composed of two uprights and a crossbar, with a section of 80×55 mm.
Installation allowed on masonry or plasterboard walls with a minimum thickness of 100 mm, with fire resistance EI 60 – REI 60. Wooden false-frame to be inserted on the masonry wall, section 25 mm (minimum) x wall thickness, or fir reinforcements to be placed between the uprights of the plasterboard wall, by the customer or direct fixing to the support. Chemolli Firebolt A1 and A2 active hinge bolts to keep the door closed in event of fire. Concealed hinges. Lock equipped with cylinder and panic handle. Intumescent gaskets installed on the frame and on the edge of the leaf and dropdown seal without threshold on the floor. Poplar plywood covering profiles.
Performance : REI/EI 60